2009 to Present
Edmonton Hospital, Edmonton, Alberta
Here we complete annual backflow testing and repairs of about 40 backflow devices ranging in size from 1/2” to 12”. This has included some big repairs over the years due to water main breaks, and sever water hammer damage.
Analysis of device failures is crucial in facilities. Over the years, we’ve implemented many procedures to help minimize device failures due to damage.
In 2013, the administration of the hospital, hired another backflow contractor to do the annual testing. They caused over $20,000 in damages and mis-diagnosed the testing results and failures. The hospital called us in to complete the repairs, and re-test all their devices. They continue to use our services to this day.